ETAP has been designed and developed for engineers to study different aspects of power systems in one integrated package.
This course is structured into 4 chapters with theory and practical examples. It is designed for protection engineers to understand the power system, short circuit concept, protection, and coordination.
Chapter 1, part 01: This part overviews different tools in ETAP with an example. ETAP offers a suite of fully integrated electrical engineering software solutions including load flow, short circuit, protection and coordination, harmonic analysis, transient stability, cable ampacity, arc flash, optimal power flow, and more. Some of these tools may not be required in our study. So we should know which part is the most important tool for us. This part overviews different parts of ETAP before starting the course. In this way, we can find the main tools and part which we should focus on it.
Chapter 1 part, 02: This part has an introduction to ETAP software. We start with creating a new project and explain different toolbars and menu in ETAP.
Chapter 1, part 03: This part overviews the main parameters of a busbar, 2 winding transformers and 3 winding transformers.
Chapter 1, part 04: This part overviews the main parameters of a transmission line and cable.
Chapter 1, part 05: This part overviews the main parameters of a static load, lumped load, and power grind.
Chapter 2, Part 01: This part shows how to study parameters with load flow analysis. To do so, we run a load flow analysis on a simple one-line diagram and study the effect of different parameters.
Chapter 2, Part 02: This part overviews load flow study case and plot option settings.
Chapter 2, Part 03: This part presents a practice to understand the parameters of load, equipment cable, busbar, cable, and transformer deeply. Then it presents load flow and load analyzer tools.
Chapter 2, part 04: This part overviews the main parameters of low voltage circuit breaker and high voltage circuit breaker.
Chapter 2, part 05: This part overviews the main parameters of an induction machine and how to model an induction machine in three different methods.
Chapter 2, part 06: This part overviews the main parameters of a synchronous generator.
Chapter 2, Part 07: This part presents a practice to understand the parameters of an induction machine and synchronous generator deeply.
Chapter 2, Part 08: This part presents how to remove the critical alarm. To do so CB overload, cable overload, and transformer overload alerts have been removed. To remove these alerts, we should know how to do cable sizing and transformer sizing in ETAP.
Chapter 3, Part 01: This part shows the effect of different parameters in the short circuit current. An induction motor can inject current to a grid even more than an equivalent generator, this part show this concept in ETAP.
Chapter 3, Part 02: This part explains the settings in the short circuit analysis. To explain the parameters of short circuit analysis and understand the short circuit modeling in ETAP, we have simulated an AG fault in PSCAD.
Chapter 3, Part 03: This part presents several duties and tools in short circuit analysis mode.
Chapter 4, Part 01: This part overviews the elements which are related to relay protection and coordination.
Chapter 4, Part 02: This part shows overcurrent parameters in ETAP and relay configurations software. The setting of overcurrent relays (P121 and distance relay SEL 421) are shown in the configuration software (Esergy studio and AcSELerator quick set software).
Chapter 4, Part 03: In this part, three-phase voltage and currents are injected to the SEL 421 with a secondary test kit (Omicron CMC 256) to explain the values in a relay and test the intravenous overcurrent function.
Chapter 4, Part 04: This part presents how to CT ratio and time delay overcurrent element (Ansi 51). Then the coordination between two relays is explained with the help of start view tools.
Chapter 4, Part 05: This part presents the coordination between three relays and how to test the coordination with the help of the sequence viewer tool.
Chapter 4, Part 06: This part explains the plot option parameters in the Star View.
Chapter 4, Part 07: This part explains how to set instantaneous overcurrent parameters (ANSI 50).
Chapter 4, Part 08: This part presents how to calculate overture ground element in ETAP and how to set these parameters in the relay.
Chapter 4, Part 09: This part presents how to add a proper fuse to a feeder and coordinate the relays with the fuse.
Chapter 4, Part 10: This part explains the protection page of the main elements and how to protect an element with an overcurrent element.
Chapter 4, Part 11: This part presents helpful tools in the protection and coordination study room.