Busbar Protection training 01 (5 min , April 14, 2022) Busbar Protection training 02 (6 min , April 14, 2022) Busbar Protection training 03 (8 min , April 14, 2022) Busbar Protection training 04 (9 min , April 19, 2022) Busbar Protection training 05 (9 min , April 27, 2022) Busbar Protection training 06 (8 min , April 27, 2022) Busbar Protection training 07 (10 min , April 27, 2022) Busbar Protection training 08 (06 min , April 27, 2022) Busbar Protection training 09 (16 min , May 01, 2022) Busbar Protection training 10 (19 min , May 01, 2022)
supplementary Files: To save your time, we’ve gathered important related files/ videos /software and attached them to the course as supplementary files.
Busbar protection REB670 2.0 IEC Application Manual Busbar protection REB670 2.0 IEC Commissioning Manual Busbar protection REB670 2.0 IEC Technical Manual SIPROTEC 4 7SS52 Distributed Numerical Busbar and Breaker Failure Protection (catalog) SIPROTEC 4 7SS52 Distributed Numerical Busbar and Breaker Failure Protection (Manual) Busbar Differential Protection, SIPROTEC 7SS60 Centralized Numerical Busbar Protection, SIPROTEC4 7SS52 Distributed Numerical Busbar, and Breaker Failure Protection, SIPROTEC 7SS50 Numerical Busbar, and Breaker Failure Protection, SIPROTEC 7VH60 High-Impedance Differential Protection Relay 01 Busbar Protection training Introduction 02 Busbar Protection training Bus Configurations 03 Busbar Protection training BB Components 04 Busbar Protection training Low Impedance Schematic1 05 Busbar Protection training Low Impedance Schematic2 06 Busbar Protection training High Impedance Schematic 07 Busbar Protection training Siemens 7SS52 08 Busbar Protection training ABB REB500 09 Busbar Protection training SINGLE Bus Without Coupler 10 Busbar Protection training Double Bus Single Breaker 2 CTs 11 Busbar Protection training Double Bus Single Breaker 1 CT 12 Busbar Protection training CT Location Aux Contacts 13 Busbar Protection training Dead Zone Load Transfer 14 Busbar Protection training Breaker Failure Protection 15 Busbar Protection training EndFault Definition Requirements 16 Busbar Protection training EndFault DoubleBus 17 Busbar Protection training EndFault 1 and Half CB 18 Busbar Protection training High Impedance BBP Setting Calculation 19 Busbar Protection training BBP Stability and Sensitivity Tests Busbar Protection All bus bar schemes in the substation-Busbar system in substation-Power system-Typical bus configuration BusBar Schemes in Electrical Substation Part 1 Bus fault cases operation explained with diagram Bus-Bar Schemes in Electrical Substation Part 2 Bus fault cases operation explained with diagram Differential protection Main and Transfer bus bar Differential Protection – Bus bar protection 7SS85 relay testing Busbar Protection Fundamentals High impedance busbar protection
IED with two low-impedance differential protection zones and eight three-phase CT inputs
Any queries, please feel free to contact us:
Course Title & Dates
Config and testing of the generator, transformer, line, and motor protection functions 4 days
Tentative Course Schedule
TIME TRAINING SCHEDULE & TOPICS 9.00am – 10.30am ABB relays, PCM 600 installation, Connectivity pack installation, Hardware configuration, Application configuration, Signal matrix Parameter setting, IED read and write IED online monitoring and signal monitoring Disturbance, and event viewer 10.30 am – 10.45 am TEA BREAK 10.45am –1.00pm SIPROTEC 5 relay families and applications DIGSI 5 and device driver installation SIPROTEC 5 configurator Relay configuration 1.00pm – 2.00pm LUNCH 2.00pm – 3.30pm SIPROTEC 4 Relay families DIGSI 4 installation Masking I/O CFC Fault Recorder 3.30pm – 3.45pm TEA BREAK 3.45pm – 5.00pm MiCOM relays range, naming, and application Easergy software Configuration and PSL Event and disturbance recorder
TIME TRAINING SCHEDULE & TOPICS 9.00am – 10.30am OMICRON CMC Test universe softwareAMT105 AMPro software signal view, impedance view, vector view different types of test modulesRIO, XRIO, and PTL 10.30 am – 10.45 am TEA BREAK 10.45am – 1.00pm Principle of Differential Protection87G Generator Differential Protection87T Trans. Differential Protection87M Motor Differential Protection87L Line Differential Protection 1.00pm – 2.00pm LUNCH 2.00pm – 3.30pm Testing of the Differential protection function (87G, 87T, 87M, 87L)Operating CharacteristicDifferential ConfigurationDifferential trip timeHarmonic 3.30pm – 3.45pm TEA BREAK 3.45pm – 5.00pm 81O Over frequency Protection81U Under frequency Protection59 Overvoltage Protection27 Under voltage ProtectionTesting of the Over/under frequency (81O/ 81U)Testing of the Over/Under voltage (59, 27)
contact us to reserve your seat
TIME TRAINING SCHEDULE & TOPICS 9.00am – 10.30am 50/51 Overcurrent protection50N/51N earth fault protection 67/67N Directional/ directional earth fault protectionRelay coordination 10.30 am – 10.45 am TEA BREAK 10.45am – 1.00pm Overcurrent test moduleOvercurrent RIO blockSettings of the Overcurrent test moduleTesting of the Overcurrent and Directional Overcurrent Functions (67, 67N, 50, 51, 50N, 51N) 1.00pm – 2.00pm LUNCH 2.00pm – 3.30pm 46 Negative Phase Sequence Protection51V Voltage-Dependent O/C Protection49S Stator Overload Protection49R Overload Protection48 Motor starting time supervision51L lock rotor 3.30pm – 3.45pm TEA BREAK 3.45pm – 5.00pm Testing of the Negative Phase Sequence ProtectionTesting of the ANSI 51V Voltage-Dependent O/C ProtectionTesting of the ANSI 49 Overload Protection
TIME TRAINING SCHEDULE & TOPICS 9.00am – 10.30am Distance protection line simulation in PSCADTesting of the fault location function 10.30 am – 10.45 am TEA BREAK 10.45am – 1.00pm 21 Line distance protection40G Field Failure Protection21G Generator Under impedance Protection78 Pole Slipping Protection 1.00pm – 2.00pm LUNCH 2.00pm – 3.30pm Distance RIO block shot Test, Check Test, Search Test, Z\t Diagram, Zone SettingsTesting of the Distance function (21)Testing of the 40G Field Failure Protection 3.30pm – 3.45pm TEA BREAK 3.45pm – 5.00pm 64S Generator, 95% &100% Stator Earth Fault Protection, 51/27 Generator, Dead Machine Protection, 24G Generator, Over flux Protection, 47G Generator, Fuse Failure Supervision, 32R Generator, Reverse Power Protection
Distance Protection Differential Protection Busbar Protection Generator Protection Restricted Earth Fault Relays Back up Relay
Our Video Training Products:
Sample discussion in our WhatsApp group, Join Us for free discussion, (Click)
The parameter set cannot be transferred to the device.
The reason for this is that the parameter for the EN100 module has not yet been updated after changing the IEC61850 system interface. To do so, open the “update” property page of the IEC61850 station and update all parameter sets. A transfer to the device now works again.
Terms of I> mean Time delay O/C, and I>> is instantaneous O/C
problem: 1ph fault but relay give 3ph command in Siemens 7SA522
Solution: In the matrix, u can raise the signal 1ph trip permitted by AR via one BI. Normally Simense relay giving always 3ph trip
Error in Siemens low Impedance busbar protection 7SS52 and alarm on bay units
for joining telegram or WhatsApp channel & groups (Click)
Our completed Courses: